Sulfite (SO3) is used in boiler and closed loop treatment as an oxygen scavenger and metal passivator. Sodium sulfite (Na2SO3) combines with oxygen to form sodium sulfate (Na2SO4):
2 Na2SO3 +O2 = 2 Na2SO4
Sulfite is a reducing agent, and will reduce iron oxide to magnetite.
In collecting a sample for sulfite testing, it is important that air not be introduced into the sample. The sample collection bottle should be filled completely to the top and then cooled prior to testing. Once the sample is opened the sulfite level should be tested immediately. If the sample is left open oxygen in the air will combine with the sulfite and result in a lower reading than is actually in the boiler or closed system.
Sulfite may be expressed as sulfite (SO3) or as sodium sulfite (Na2SO3). 1 ppm sulfite (SO3) equals 1.575 ppm of sodium sulfite (Na2SO3).
Sulfite may be removed from water by aeration.
IBH Labs brings you the water treatment technology you need at a price you can afford